Riello UPS Introduces NextEnergy, the latest UPS series designed for mission critical applications. The three phase UPS offers transformerless double conversion technology VFI SS 111, with integrated IGBT three-level design.
NextEnergy is designed to meet the power requirements of tomorrow, offering high efficiency and low running cost. Thanks to the Efficiency Control System, NextEnergy also guarantees the highest levels of efficiency even at partial loads. Its unity power factor and easy system upgrading make it the ideal solution for the business continuity of any IT application. Zero impact source NextEnergy is designed with the latest technology to not only prevent disturbances on the mains but clean the power e.g.. Harmonics generated by non-linear loads.
The input AC/DC converter is based on the IGBT rectifier design using the latest 3-level technology. The key features are:
Thanks to the programmable maximum input power (kW or kVA), NextEnergy can be installed into AC supply systems with limited power availability such as a diesel generator or contractually reduced power sources, andthen supply the additional power required using the batteries (peak demand function). Outstanding performances
This is thanks to the automatic speed control which constantly adjusts to the specific load level, the fan failure alarm and the fan redundancy – with condition apply.
Battery care system
The battery is one of the most important parts of the UPS that ensures the correct operation in case of mains failure. NextEnergy includes all the latest features to prolong the battery life and keep the battery working efficiently, as well as advising users about any potential problem. The variety of charging methods allows the use of the most common type of battery and technologies available on the market such as VLRA, AGM, GEL, NicCd etc. In addition to the flexibility of the battery cells, NextEnergy allows users to choose the most cost-effective solution for the required back-up time. The battery charging and discharging is assured by the STEP-UP/ STEP-DOWN converter which means that when the batteries are charged and the mains is available, the converter is no longer connected to the supply. This means the ripple current is practically zero which leads to a significant improvement in battery life.
Operation without Neutral
NextEnergy can work with or without the neutral connection. This is an important feature to reduce the TCO of the distribution system where the neutral is created by an isolation transformer close to the load. For example, in the modern Data Centre, or where the neutral is not used at all. The major benefit being a reduced cost of the distribution arrangements.
Maximum reliability and availability
NextEnergy UPS can be connected in parallel with up to 8 units to increase the capacity or add redundancy (N+1). Considering that a typical load can vary from 20 to 80%, the Efficiency Control System (ECS) function optimises the operating efficiency of the entire system according to the power absorbed by the load. This ensures higher overall efficiency during all load conditions. Hot System Expansion (HSE) allows the addition of further UPS into an existing system, without the need to switch off the operational units or transfer them to bypass mode. This guarantees maximum load protection, even during maintenance and system expansion. It ensures maximum levels of availability – even in the event of an interruption to the parallel control cable the system is “FAULT TOLERANT”. It is not affected by connection cable faults and continues powering the load without disruption, signaling an alarm condition.
Interactive Touch Screen
NextEnergy is equipped with a Touch screen 7” graphic display (800×480 pixels) providing UPS information, measurements, voltage and current waveforms, operating states and alarms in different languages. The default screen displays the UPS status, graphically indicating the status of the various assemblies (rectifier, batteries, inverter, bypass). Also, the panel is used for configuration and setting the parameters of the UPS with 3 levels of the security password.
NextEnergy offers the capability to work with the advanced multi-platform communications for all the latest operating systems and network environments.
|MODEL||ΝΧΕ 250||ΝΧΕ 300||ΝΧΕ 400||ΝΧΕ 500||ΝΧΕ 600|
|Nominal Voltage||380-400-415 VAC three-phase|
|Voltage Tolerance||+20% -40% (conditions applied)|
|Soft Start||0-100% in 120 sec (selectable)|
|Standard Equipment Provided||Back feed preotection, seperate bypass line|
|Type||VRLA AGM / GEL, NiCd, Supercaps, Lion, Flywheels|
|Recharge Voltage Compensation||-0.11Vx° C|
|Nominal Power (KVA)||250||300||400||500||600|
|Active Power (KW)||250||300||400||500||600|
|Number of Phases||3+Ν|
|Nominal Voltage||380-400-415 VAC Three phase + N|
|Dynamic Stability||±5% in 10ms|
|Volotage Distortion||<1% with linear load /<3% with non-linear load|
|Frequency Stability on Battery||±0,05%|
|Frequency||50 or 60 Hz (selectable)|
|Overload||110% for 60′; 125% for 10′;150% for 20 seconds||110% for 60′; 125% for 10′;150% for 1 minute||110% for 60′ ; 125 for 2′ ; 150% for 20 seconds||110% for 60′ ; 125 for 10′ ; 150% for 1 min.|
|Nominal Voltage||380-400-415 VAC three phase +N|
|Nominal Frequency||50 or 60 Hz (selectable)|
|Frequency Tolerance||± 2% (selectable from ± 1% έως 5 %)|
INFO FOR INSTALLATION
|DImensions (WxDxH) (mm)||800 x 850 x 1900||1200 x 850 x 1900||1400 x 850 x 1900||1600 x 850 x 1900||2000 x 850 x 1900|
|Input Cable||Bottom||Up and Bottom||Up and Bottom||Bottom||Bottom|
|Remote Signals||Volt-free contract (configurable)|
|Remote Controls||EPO, bypass and another spare|
|Communications||USB + Dry contacts 2 slots for communications cards|
|Operating Temperature||0 ° C/ +40 ° C|
|Relative Humidity||5 to 95% non-condensing|
|Color||Dark grey RAL 7016|
|IP Rating||IP 20 (other on request)|
|Efficiency (AC-AC) – On Line Mode||Up to 97%|
|Standars||Safety: EN 62040 -1 (directive 2014/35/UE); EMC: EN 62040 -2 (directive 2014/30UE)|
|Classification in accordance with IEC 62040-3||(Voltage Frequency Independent) VFI – SS- 111|
|MOving the UPS||Pallet|
Download the Pdf here